Office Fitout Best Practices
Not every business has the luxury of operating from modern, purpose-built premises which use the best layout and power, cabling and hardware infrastructure. And it can be impractical to transform an older building or tenancy while the business is operating. But when moving premises, or refreshing premises is an excellent opportunity to set things up for the best results. Many computing problems are caused by bad power or inefficient network cabling.
Power: Count devices for each workstation and then add 50%. For example: desktop computer/laptop, monitor, phone charger, personal printer. That's four, so you'd want six at each workstation. That would accommodate addition of a second monitor, label printer etc.
Or, depending on the layout, four at each workstation, and then some extra communal power points to share amongst a group of 4-6 people.
Power point assemblies are now available with embedded USB charging ports, so this can reduce the need for standalone power points to accommodate smartphone and tablet charging.
The aim is to reduce to zero the number of power boards required.
Minimum two data points per workstation, one each for computer and telephony. Some phone handsets have an inbuilt switch but this forces the workstations to use much slower connections, so each device having a dedicated data point is very important. If workstations are clustered, have 1-2 spare data points for each cluster.
Additonal data points in common areas for printers, wireless access points, surveillance cameras.
Server / Comms Room
Consider future network expansion. Size the switch hardware by counting the active data ports, adding 50% and then rounding up to the nearest appropriate device. For example, suppose you count 15 data points, and an additional data point for the router, that suggests a 16-port switch. But in that circumstance, the device would be full immediately. So add 50%, which yields a 24-port device. If the port count is 22, add 50%, which is 33, and then round up to the next size router, 48 ports. (Of course, it is possible to add switches to accommodate network expansion, but this requires space in the comms rack which may not be available, draws more power and creates a bottleneck via the link between switches.)
Switches should have some power-over-ethernet (PoE) ports for wireless access points, IP cameras and such.
Use Cat6 cabling.
Uninterruptible power supplies may not behave properly when attached to power points linked to safety switches. Consult your electrician. In the communications/server room it may be necessary to have some dedicated power outlets for UPS devices which will not conflict with safety switches.
Data and power, ideally located so devices can be plugged in without running a cable across traffic areas.
Will often have dedicated projector/computer equipment so data and power need to be located appropriately. Also additional data and power around the edges. Inbuilt USB charging sockets for guests.
Power and data points located centrally in the floor.
Boardroom table should have central gap, so devices can run their cabling outwards into the centrally-placed data/power points. Ideally half a dozen power points and data points depending on expected use for the room.
Bathrooms/Toilets/Kitchens/Dishwashers. Consider what would happen if there was a flood due to blocked pipes etc. Where would the water go? Could it reach the communications room, where servers and comms equipment is kept?
In many small businesses, the communications cabinet would have equipment located at the top of the cabinet, so inundation of water would not affect it. But if you have so much equipment the entire cabinet is being used, consider the water risk. Perhaps two smaller cabinets, mounted at a reasonable height, is more appropriate. Also be sure that power and data incoming to the comms cabinet is up high.
Air Conditioner / Hot Water System
These units are sometimes in ceiling spaces. If they leak, water may damage equipment. Be sure that these are located where water leaks will not affect servers and communications. Better still, be sure they are located on the outside of the premises (eg wall-mounted instantaneous heating).
Always assume the air conditioner or hot water will leak one day, and design appropriately.